...of the person carrying out the inspection to allocate an appropriate code (C1, C2, C3 or FI) to each of the defects found during the inspection.
The person carrying out the inspection should have an in-depth knowledge of the current version of BS 7671 IET Wiring Regulations and Guidance Note 3 Inspection & Testing. Depending on the type of electrical installation other BS Standards and Approved Building Documents may also apply.
In addition to the above requirements the electrical inspector should be fully competent, highly skilled, suitably qualified and extensively experienced in testing and inspecting the particular type of electrical installation they are reporting on.
EICR Observation Codes
The four main Condition Report observation codes are Code 1 (C1), Code 2 (C2), Code 3 (C3) and Further Investigation (FI).
A code 1 observation must be rectified and made safe without delay.
An example of a C1 observation (it's dangerous now!) would be the cover of a consumer unit missing hence exposing live parts. Any exposed live parts such as an open consumer unit busbar or an exposed live cable end would be classed as a code 1, as it is dangerous (right now) at the time of the inspection.
A code 2 observation must be rectified as a matter of urgency.
An example of a C2 observation (potentially dangerous) would be no RCD protection to an external 13A socket. A C2 potentially dangerous observation extends to any potential dangers, hazards or risks which could occur under certain conditions or under fault conditions such as, this could become dangerous should that happen.
A C3 observation is your recommendation for improvement.
A code 3 would be an observation you feel warrants a mention on the report of something you feel should be improved but would not be classed as a C1, C2 or FI.
An FI observation must be investigated as a matter of urgency.
Further investigation would be allocated to an observation which could be potentially dangerous but could not be determined at the time of the inspection, therefore requires further investigation into the defect to be able to determine what code to allocate against it.
EICR - Pass or Fail ?
It is the responsibility of the person carrying out the inspection and testing to determine and allocate either a C1, C2, C3 or FI to each defect / non-compliance found (if any) in their professional judgement.
Professional judgement means the application of relevant training, knowledge and experience, within the context provided by auditing, accounting and ethical standards, in making informed decisions about the courses of action that are appropriate in the circumstances of the audit engagement.
There are only two outcomes of an Electrical Installation Condition Report formally known as a Periodic Inspection Report (PIR), they are SATISFACTORY and UNSATISFACTORY (for continued use).
If an observation has been allocated either a C1, C2 or FI code then the installation must be deemed to be unsatisfactory. If no code 1's, 2's or FI's have been noted but a number of code 3 observations have been made then the installation can be deemed to be satisfactory as long as the inspection and testing has been carried out thoroughly and there are not too many limitations (LIM) applied.
EICR - Limitations (LIM)
Many inspection reports may include "LIM" meaning a limitation has been applied to the inspection.
A limitation (LIM) noted on a condition report means that a particular item(s) and / or circuit(s) have not been tested or inspected. This could be due to no access to a particular area of the installation such as a server room, therefore the circuit supplying the server room could not be tested or inspected hence a limitation has been applied.
Another example of a limitation could include high level warehouse lighting, if there is no safe working access to the high level lighting then a limitation might be applied.
The Work at Height Regulations 2005 apply to all work at height, where there is risk of a fall liable to cause personal injury. They place duties on employers, and those who control any work at height activity (such as facilities managers or building owners who may contract others to work at height)
If an electrical installation which contains any limitations has been assessed to be satisfactory, the satisfactory assessment is subject to the limitations contained within the report, meaning the satisfactory condition is only applicable to the circuits which have actually been tested and inspected and does not include the limitations applied.
EICR - Software for Installation Condition Reports
In the age of fast moving technology there seams to be an app for almost everything these days and that includes apps for Electrical Testing & Certification. Our new Pro Certs App is available on iPad, iPad Mini, Android Tablets and Windows 10 devices and is free to download.
Coding Observations - Difference of Opinions
Many electricians and engineers interpret the regulations differently and have different opinions in the coding of observations for a condition report. Join our free forum topic on "EICR - Coding Observations" to share what you have encountered during your work inspecting electrical installations.
Join our Newsletter