The included MCCB Zs charts includes various MCCB's, Frames and types from a variety of manufactures. In addition of the MCCB charts also included are the common BS EN 60898, 3871, 61009, BS 88 fuses, RCBO's and MCB's along with many more.
MCCB Zs Charts PDF
Max Zs for 60974-2 MCCB
If you have any specific MCCB Zs charts you would like us to add to the Max Zs app then please send them to firstname.lastname@example.org. Please ensure the tables are to the current version of the wiring regulations and factor in the Cmin factor @ 230V. The Cmin factor is 230 x 0.95 = 218.5 volts, thefore to calculate Zs: 230 x 0.95 = 218.5, 218.5 / la = Zs.
Many MCCB's can be adjusted to suit individual requirements, the settings of an MCCB can affect the maximum permitted Zs value. The setting of an MCCB can include I2t, Ir, lsd, li, lg, xIn. The settings are for over current protection (Ir), over current protection time setting (tr), short circuit protection (lsd), short circuit time delay (Tsd), instantaneous current setting (li), earth fault protection or ground fault protection (lg).
Refer to the manufactures documentation on how to correctly set up the MCCB settings.
Smart Electrical Apps for the Smart Electrician
Join our Newsletter